I want to talk about how to keep the lights on when the grid fails, something a lot of people were thinking about when that major winter storm rolled over much of the United States during the holidays and then when another hammered California and the southern part of the country, leaving millions of people without power, and sometimes even trapped in their homes.
This is going to be a two part series. I’m going to talk about the AC200MAX first because there are several people waiting for the review of this device. The second part is going to talk about these portable power systems in general, why you might want one, and most importantly how to determine how to properly size it to suit your needs without wasting money and, even worse, getting mislead by the advertising.
These things are often mislabeled “solar generators”, but they are neither solar nor generators. If you buy the almost always optional solar panels to recharge these devices you could make the argument they’re solar generators I suppose. But these devices by themselves are really energy storage devices. Basically they’re a big box of batteries.
Bluetti has been around for a few years now and its PPSs (portable power stations) are generally rated well in reviews and so far my experience with the one in the photo above has been completely positive.
The model I picked, the AC200MAX has a capacity of 2048 watt hours, and it can handle a maximum sustained load of 2,000 watts, and can handle brief surges in demand of up to 4,000 watts. It has a built in inverter that converts the batteries DC power to 120VAC. There are four standard 120 VAC plugs on the front. It also has a 30 Amp 120V NEMA TT-30 connector typically seen in RVs that would let it power an entire RV.
It also has a variety of DC power ports including USB-A 5V 3A, two USB A 18W ports, a 100W USB-C port, a DC 12V 10A cigarette lighter type plug in port, a DC 12V 30 Amp port, and as if that wasn’t enough, there are two wireless 15W charging pads for cellphones on the top of the box.
Basically this thing has just about every kind of power plug I’ve ever heard of. All of the outputs have overload and short circuit protection. And no, I did not test that. I’m not about to deliberately short circuit a device that cost me almost two grand just to see if the protection actually works.
On the lower left side of the unit are there are two connectors to hook up optional external battery packs. Up to two optional battery modules, either a 2048Wh ($1,300) or 3072Wh ($2,200) battery packs can be added to the unit to that can give it a total capacity of more than 8,000 Wh. And that, folks, is a hell of a lot of energy to be packed into that small of a space.
Also on the left side of the unit are the charging ports. You have several options here too for charging. The unit can be charged by, well, just about anything. It comes with a 500 watt charger for topping off the AC200 from the grid and it will charge up the unit reasonably quickly. The single AC charger will replenish the AC200MAX in about 5 – 6 hours.
There is also a DC input port intended for use with an optional solar charging system. There is a solar charge controller built into the AC200. That port can also be used to recharge the unit from a car with an optional cable (I’m not sure how long that would take but at least it’s an available option).
If that’s not enough options for you and you need to recharge the AC200 even faster, you can pick up a second 500 watt charger and with an optional cable charge the unit with two chargers at once, one plugged into the solar charging port. Or you can charge it at the same time from a solar panel system and the AC charger.
If you plan on getting solar panels for recharging the device it can handle up to 145V and 15.2 Amps maximum without the need for an external charge controller.
The manual claims you can recharge this thing by plugging a cable into a car’s cigarette lighter. Considering those things only put out about 120 watts, be prepared to wait a while to do a recharge. But still it’s an interesting feature that might be useful.
Physically, this thing is a beast. It is as large and heavy as my Yamaha 2KW gasoline powered inverter. It weighs in at about 60lbs, and the physical dimensions are around 17″ X 11″ X 15″. At 60 pounds you aren’t going to be casually carrying this thing around. If you end up getting the optional expansion battery packs this thing is going to be seriously heavy. But the weight and size is typical for portable power stations with this capacity.
Oh, and I should talk about the batteries. This unit uses LiFePO4 batteries. The manufacturer claims that after 3,500 charge cycles the batteries should still retain about 80% of their original capacity. That means you could recharge this thing every day for 10 years and still have 80% capacity left.
Now we come to the control systems. Just left of the screen is a big ON button. Push that and after a moment it will boot up and the color touch screen turns on. The screen not only displays all of the information you need, it is the primary control system for the unit.
Before you can use it you have to specifically turn on the DC and/or AC power systems to make the plugs “live”. But once you do that it’s ready to go and all you need to do is plug in whatever devices or appliances you need to power.
Other information is also available on various screens including load statistics, the ability to switch the system to handle European or Japanese electrical devices which use a different power system, and a few other goodies.
And there is a free app you can get for your phone that allows you to monitor what the Bluetti is doing. It is Bluetooth only, the device has no WiFi capabilities, so the range is limited. I was able to keep in touch with the Bluetti with my phone anywhere I was in the house, garage and even much of my backyard.
How well does it work?
If you thought all of the above was boring, you’re going to find the actual in-use evaluation of the Bluetti even more dull. It just works exactly as specified by the manufacturer. No drama, no problems, no issues, nothing. It just did everything it was supposed to do without any problems at all.
The primary use for mine is to provide backup power for two essential systems in the house, our gas furnace and our sump pumps. So that’s what I’ve been testing it on.
A gas furnace doesn’t use a lot of electricity, just enough to keep the thermostat system operating, which is minimal, and, of course, the blower fans. The actual heating is done by the combustion of natural gas. A natural gas furnace doesn’t use a great deal of electricity, generally in the 350 – 700 watt range. The electronic igniter that actually lights the gas uses some electricity of course. Rather a lot, in fact, but it works for such a short period of time that it isn’t that important.
My furnace was already set up to be used with our backup generator so I didn’t have to do any additional electrical work to make it possible to power the furnace alone. All I have to do was turn off the furnace, plug in a single electrical cable to switch from grid power to the Bluetti, and turn the furnace back on again.
Sidenote: I am going to give the usual disclaimer here. Consult with a licensed electrician before trying to make any modifications to your house’s electrical systems. Yes, I know house wiring isn’t that difficult to deal with, but unless you know what you’re doing you can end up in serious trouble or even dead if you screw something up. Then there is the legal issues to consider. A lot of jurisdictions require a licensed electrician to make any significant changes to a home’s electrical systems. There are also issues when it comes to your home owner’s insurance. If there is a fire in your home and subsequent investigation reveals that the home had electrical modifications that did not meet building codes or that were not performed by a licensed electrician the insurance company may refuse to cover the damage.
So, how did the Bluetti work while powering the furnace? Exactly as I expected it would. It handled the furnace easily with no issues at all. As my research indicated, the furnace required about 350 – 550 watts during operation. The wide range there is because this model furnace has a variable speed blower fan.
Once you know how much power a device draws, figuring out how long a battery system will run that device is pretty simple. The Bluetti has a bit more than 2,000 watt hour capacity so it should be able to run a device that needs, on average, about 400 watts, for about 5 hours. But that’s assuming that the device will be running all the time, and the furnace isn’t running constantly. The fans only run when the furnace’s burner is actually in use. On the day I did this test after 3 hours of operating the furnace the Bluetti still had 78% capacity, far better than I had anticipated.
So in actual testing, with those particular weather conditions, with the thermostat set at 67F degrees, the Bluetti should have been able to keep the furnace operating for around 12 hours.
Those numbers are under a specific set of conditions that could change quickly, of course. The weather was relatively mild with outdoor temperatures about 30F and very little wind. During colder weather and higher winds the furnace would run more often and for longer periods of time in order to maintain the temperature in the house. That, of course, would deplete the Bluetti more quickly.
The other intended use for the Bluetti is to keep the sump pumps going. We had part of the basement flood because of a sump pump failure here some years ago and we do not want to go through that again. I now have a backup pump on the shelf along with all of the tools and plumbing parts I need, and I changed the whole system so I can swap out a pump in just a few minutes. But in case of a power failure that isn’t going to do me any good. And since power failures often happen during storms when we’re getting heavy rain, they can happen at the worst possible time when we need the pumps the most.
Sump pumps require considerably more power than the furnace. The pumps I have require about 700 watts to run, but they run only intermittently. In addition to that load, there is a significant surge current when the pump first starts up, with can hit 1,300 watts for a few seconds.
I picked the capacity of the Bluetti specifically so it could, hopefully, handle both sump pumps at the same time. It can handle a current demand of up to 2,000 watts, sustained and the pumps together would take about 1,400. The PPS can handle a surge demand of over 4,000 watts. In a worst case scenario the two pumps might start at exactly the same time so there would be a momentary surge demand of about 2,600 watts. So it should be able to handle both pumps, at the same time, even if both pumps start at the same time.
I did test the Bluetti running the pumps. I already knew that because of the surge load and increased power requirements I would get much less actual runtime on the pumps than I would with the furnace. And I was a bit anxious about it being to able to run both pumps at the same time, especially if both started at exactly the same time. I’m pleased to report that it was able to handle both pumps with no problems. The Bluetti’s internal cooling fans did come on while running the pumps, but that was expected and normal.
During an actual rainstorm situation the Bluetti wouldn’t be able to keep both pumps running for more than an hour or so I estimate, but that’s all I need from it. I want it to give me some breathing room, carry the load for a while until I have a chance to get one of the gasoline generators running. My big Generac is cranky and hard to start sometimes, and even my little 2KW Yamaha inverter takes a while to get set up in a good location outside and run a cable down to the basement.
Could it run both of the pumps and the furnace at the same time? Well, maybe? That would be pushing the Bluetti to its full capacity, though. Theoretically it could. Total sustained demand running all three at the same time would be about 1,900 watts, maybe a bit more, really close to it’s top limit of 2,000 watts sustained load, and in a worst case scenario where both pumps and the furnace would start up at exactly the same time the surge load would be pushing the theoretical limits of the device’s maximum surge capacity.
Hopefully that won’t be necessary to deal with. Usually during the heating season the pumps don’t run at all. They’re generally only needed in the spring, summer and fall, and then only when we have a significant rain event.
Now, what about recharging this thing? At the moment I’m using the grid powered 500 watt charger that came with the unit. Bluetti will sell you solar panels that are capable of recharging this unit in a reasonable amount of time, but there are problems with that system. First it’s expensive, Buetti’s system will cost you $800+ for enough capacity. And even worse, these are portable, non-weather proof and not intended to be left outside. They can’t be left up in rain or snow. That’s not what I’m looking for. I want to set up a solar charging system that will be more or less a permanent installation that I don’t need to worry about. I’m still looking into that. I’ll probably set something up this spring when I can get outside to work.
So let’s sum everything up. The Bluetti AC200MAX is a very well made piece of equipment, it works exactly as advertised. I’ve encountered no problems at all with it during testing. It has met and even exceeded my expectations all the way around and I am very pleased with it. Yes, it’s heavy and awkward to lug around but so is any PPS with this capacity. It just plain works, and works well.
This thing ain’t cheap, and this may be a deal breaker for a lot of people. The Bluetti model I’ve been talking about cost me, including taxes, $2,000. That’s a heck of a lot of money, especially when you can get a gasoline powered generator with the same capacity or even more for a quarter of that price. So before you buy one of these you need to consider all of your options and what your needs are.
In our case here, we feel it was worth the money even though we have gasoline powered generators. The Bluetti takes some of the panic out of the situation. If necessary it could keep the essentials, the furnace and pumps, running long enough to give me a chance to get one of the gas generators set up and running. And I was also thinking of MrsGF if I didn’t happen to be home when there was a power failure. There’s no way she could get the big Generac set up and running by herself and there’s a good chance she couldn’t get the little 2KW Yamaha running either. With the Bluetti all she has to do is turn it on and plug in some electrical cords and she has some time to figure out what to do. And she would have some, oh, buffer time, let’s call it, to possibly get out the little Yamaha generator and get it running to take over if the outage lasts more than a couple of hours.
Long Term Plans
I’m looking into a solar panel system to keep it charged but at this point I don’t know what that is going to be. I want something that can be semi-permanently mounted on the roof of the garage where it is out of the way and I don’t need to worry about it. I’m looking for a system that would give me a minimum of 800 – 1,000 watts and that would be easily expandable because I’m seriously considering trying to make at least some of the household independent of the grid, not for any particular reason but just because I want to.
I’m considering getting another PPS, not necessarily another Bluetti, and using that as the primary power source to run my entire combined office, radio shack, electronics work area, charged by solar panels on the roof and/or on the south facing wall of the garage. How far that project will go depends on how ambitious I get and what my budget looks like.
Comments and questions are always welcome.
6 thoughts on “A Look At The Bluetti AC200MAX Portable Power Station”
I like it. Are you prohibited from using solar panels you can buy elsewhere? Warranty-wise?
Nope, there’s no restrictions on tha as far as I can tell when going through the info provided with the unit. All things considered the Bluetti panels aren’t bad and the pricing isn’t horrible, but I don’t like the fact that they aren’t weather proof and are intended for temporary use. I’d probably be aiming for about 1,000 watts of solar panels, not just to feed the Bluetti but to also feed whatever system I eventually install to run my office/lab/radio room in the basement.
My biggest problem keeping them charged is going to be the weather. From about November through into March we in cloudy conditions for days at a time. Energy production from solar panels drops by as much as 80% when it’s cloudy. Anyway, we’ll see what I eventually come up with. I’m still researching and looking into suppliers.
That’s a really nice unit; I am especially impressed with the touch screen interface. I look forward to a follow up.
Overall I think it is very, very nice. And it seems quite robust too. I haven’t tried it myself but in one test they ran it up to 2,600 watts output before it overloaded and tripped out. I ran into one video on Youtube where a fellow had a rather odd setup. He had the AC200MAX and the two add on expansion batteries. He was using the Bluetti to recharge his primary battery system that ran his shop, with the Bluetti hooked to something like 1,200 watts of solar panels, and running it 24/7 feeding his primary system. During daylight hours once the Blue system was fully charged it was dumping the current straight thru to his primary battery system, then running off the Bluetti at night. Exactly why he had it set up this way I have no idea.
At first glance, this device looks like something that no household should be without.
Something like this would be a good thing to have around just in case, and if you don’t want the hassle of dealing with a gas powered generator. The biggest problem with them is that when start to get up into the energy storage capacity that you need to handle anything serious prices go up real fast.
LikeLiked by 1 person